The message MAX TEMP REACHED is short for the output circuit is no longer a closed circuit allowing for power to leave EDDI.
This, in turn, means, if your water is cold, the device you are powering from Eddi may have tripped.
A good test to do is to place Eddi into BYPASS (switch at the bottom to the right) and leave it an hour, if the water is still cold this is most likely the output device fault rather than Eddi's.
If you find the water is still cold after a BYPASS period of circa one hour please do get in touch with our Technical Support Team at Support@myenergi.com or Call 0333 300 0313
If you find the water is at temperature, Eddi is working as expected.
Article is closed for comments.